Replaced bad contactor on the outdoor unit. It was keeping the compressor from running.
Found and ordered a control board for this unit. It was not allowing the heat pump to defrost and caused the ice build up.
Customer complained of a musty moldy smell. Checked duct system for leaks, checked each register where it penetrated the floor of the home, also checked return air for leaks and the evaporator coil to be sure it was clean. Heating Company serving Verbena, AL
On the left you can see a very dirty condenser coil and on the right you see a chemically cleaned coil. This unit could not breath and wasn’t working properly. This customer signed up for our twice a year maintenance after feeling the difference a clean coil offers your comfort.
Completing service and check!
Installed a new condensing unit for this customer.
Service call outdoor unit not running.. bad capacitor..
Checking out this trane heat pump system.. good system running like it’s supposed to be.. checking ref electric and all good..
Ice machine not making ice. Replaced bad curtain switch and checked out. Light Refrigeration repairs and ac in Clanton.
Church AC Repair. Found a tripped breaker for an air handler above the drop ceiling in the sanctuary. To avoid moving pews before tomorrow’s service I will come back Monday to check the unit out.
Change indoor txv for a great customer of Giles.. got the unit back cooling and everything is all good..
Got to replace indoor coil..
Mini split dirty coils
Found bad capacitor on the outdoor unit.